- Our Products
- Fire Detectors
- Gas Detectors
- Control Panels
- Custom Gas Detectors
- Custom Systems
- About Us
- Customer Support
- Industry News
- Contact Us
T301 Fixed Temperature Rate Compensated Heat Detector with Normally Closed Contact Type has been the industry standard for over 25 years. Use to detect over-temperature conditions produced by fires. This item is explosion proof for use in hazardous locations, and features all-metal construction. Use in any locations requiring a fail-safe alarm circuit. Available in wide range of temperature settings from 140°F/60°C up to 450°F/232°C.
The SST Model T301 detectors are highly reliable thermal detection devices which have been a standard of the fire protection industry for over 30 years. They may be used as an alarm device, to sense overheat or fire and alert personnel via the Safety Systems VulcanGuard Fire Detection and Control System, or they may be used to sense a fire and actuate the release of extinguishing agent. These units are designed with rate compensation. This provides a unique advantage over both fixed temperature and rate-of-rise types of detectors, allowing these detectors to accurately sense the surrounding air temperature regardless of the fire growth rate. Fixed temperature detectors must be completely heated to alarm temperature before responding, and therefore, a disastrous time lag may occur with a fast rate fire. Rateof- rise devices, on the other hand, are triggered by the rate of increase in ambient temperature and are subject to false alarms caused by harmless transient thermal gradients, such as the rush of warm air from a process oven. By contrast, the SST Model T301 fixed temperature rate compensated detectors have the inherent ability to operate whenever the surrounding air temperature reaches the selected protection level, even if this rise is so fast that the body of the detector is not completely heated. At the same time, the SST detectors will not respond to sudden temperature changes below the selected rating of the detector.
The Model T301 Fixed Temperature Rate Compensated Heat Detectors are designed for use in both “ordinary” and hazardous locations. For ordinary use, they may be mounted to any standard electrical junction box with a 7/8 inch opening using a standard electrician’s connector nut. For hazardous locations, where “explosion-proof” construction is required, the detectors must be installed in a 1/2 inch threaded opening in a suitable listed fitting in accordance with the National Electric Code and/or the local authority having jurisdiction.
To meet the spacing requirements of UL for these detectors, they should be spaced no more than 25 feet apart in the protected area. This rating is based on being located on a smooth ceiling, with the distance between the detector and any wall or partition no more than 12.5 feet. In open joist or beam construction, closer spacing is required. For applications in normal areas where ceiling temperatures do not normally exceed 100°F, the 140°F rated detector is recommended. For all other areas, the temperature rating of the selected detector should be 50 to 100 degrees greater than the highest expected ambient temperature. The end of the detector is color coded according to the rated temperature. This is to allow easy inspection after initial installation for proper temperature range.
LIFE SAFETY: Heat detectors protect property only. In most fires, hazardous levels of smoke, heat and toxic gasses can build up before a heat detector would initiate an alarm. In cases where life safety is a factor, smoke detectors are recommended.
Thermal (Heat) fire detection capability shall be provided by fixed temperature rate compensated heat detectors for locations indicated on the plans. The detectors shall be self restoring, and designed to activate at the rated temperature regardless of the rate of fire propagation. Fixed temperature detectors without rate compensation or rate-of-rise detectors shall not be acceptable. Stainless steel hermetically sealed construction shall be used to insure corrosion resistance and reliability. The detector shall be UL listed approved for use in Class I, Groups B, C or D and Class II, Groups E, F or G hazardous locations. The specified detector shall meet the seismic requirements of IEEE standard 334. Safety Systems Technology Model T301 Fixed Temperature Rate Compensated Heat Detectors, or approved equivalents, shall be supplied.
Q. An existing heat detector over a commercial fryer is being activated. What can be done to prevent false alarms?
A. The heat detector is designed to respond when the temperature is reached. Also, as the fryer becomes hot the heat will travel upwards and accumulate towards the ceiling. Detectors located close to where the heat accumulates may trigger the detector when the set temperature is reached. There are also various factors that may affect the operation of the heat detector such as improper installation. Please consult the instruction manual to determine the proper installation.
|Detection Method:||Fixed Temperature Rate compensated thermal (heat) detector Provides faster and more reliable fire detection than other types, with no tendency to false alarm.|
|Rated Alarm Temperature:||Factory preset See ordering information for available settings.|
|Contact Type:||Normally Closed, self restoring Contact opens when air temperature is greater than the rated alarm temperature, and recloses when temperature falls below the rated temperature.|
|Contact rating:||24 VDC 2 Amps When used with VulcanGuard or NOVA-5000 System, switched current is limited to 24 mA by 1000 ohm “in-line” resistor in series with contact.|
|Material:||Stainless Steel sensing shell Color coded paint on end to identify temperature range.|
|Hazardous Locations:||Class I Groups B,C,D, and Class II Groups E,F,G. May also be used in non-hazardous locations.|
|Size/Weight:||0.63 inch diameter, 3.66 inches long, 5.4 ounces Extends 1.25 inches into junction box.|
The temperature rating of the selected detector should be 50 to 100 degrees F greater than the highest expected ambient temperature.
|301-140||Model T301 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 140°F, 60°C.|
|301-160||Model T301 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 160°F, 71°C.|
|301-190||Model T300 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 190°F, 88°C.|
|301-210||Model T300 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 210°F, 99°C.|
|301-225||Model T300 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 225°F, 107°C.|
|301-275||Model T300 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 275°F, 135°C.|
|301-325||Model T300 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 325°F, 163°C.|
|301-360||Model T300 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 360°F, 182°C.|
|301-450||Model T300 Normally Closed Contact Fixed Temperature Rate Compensated Heat Detector, 450°F, 232°C.|